The project consists of a two-level 25,572 SF (6,131 2nd level mech. space) Tier III data center designed to TIA-942 and NFPA 75 guidelines. The main data floor is split into areas, 3,600 SF each. The design is based on 1600 KW total future load (800 KW per area). This phase included a 480 KW build out of the north pod (96 racks*5 KW/rack=480 KW). Mechanical pads, precast openings, conduit paths, and pipe sizes were installed to accommodate future build outs. The data portion of the building is constructed of architectural precast walls and structural precast roof. The office portion is structural steel with a metal panel and brick veneer. Both were constructed on top of footing and foundation wall provided by a previous contractor. The previous contractor also installed the first lift of asphalt and curb and gutter. All other work was by McGough. The Marshfield Clinic Data Center did not require Raised Floor.
Marshfield Clinic Data Center
14,500 square feet